- MARKET SECTORS
- Dan Holohan: Heating Help
- Morris Beschloss: The Beschloss Perspective
- Hank Darlington: Showrooms
- Jim Wheeler: HVAC
- Rick Johnson: Distribution Management
- Dick Friedman: Tech Tips
- Mike Miazga: In Closing
- Safety Columnists
- ASA President’s Letter
- Josh Brown: Generation Y Insights
- Dirk Beveridge: Innovation Strategies
- PVF OUTLOOK
- PB OUTLOOK
- Premier 150
- Rep Locator
- B.I.G. Book
- American Supply Association
- Industry Calendar
- Classified Ads
- Supply House Times Store
- Industry Links
- Custom Content & Marketing Services
- Market Research
- Plumbing Group
- BATH & KITCHEN PRO
The U.S. Consumer Product Safety Commission, Health Canada and Unitary Products Group, a division of York International, announced a voluntary recall of Coleman, Coleman Evcon and Red T gas furnaces used in manufactured homes. About 223,600 were sold in the United States and 2,400 were sold in Canada (previously recalled in November 2004).
The furnace can overheat and cause the heat-exchanger to crack and create openings that allow flames to be exposed. When this happens, drywall and other nearby combustibles are exposed to the flames, posing a fire and smoke hazard to consumers.
The firm has received reports of 393 incidents, including some involving extensive property damage that could be related to these hazards; 366 of those reports were received after the November 2004 recall announcement. No injuries have been reported.
The recall involves Coleman, Coleman Evcon and Red T brand furnaces sold nationwide between 1995 and 2000 as original equipment in manufactured homes and as replacement furnaces in manufactured homes. The furnaces are silver with white access panels. “Coleman,” “Coleman Evcon” and “Red T” brand names are located on the middle of the front access panel. The model number is written on a faceplate, found by removing both front access panels. The faceplate is found mounted on the left inside surface behind the lower panel.
Models included in the recall are: DGAM075BDD, DGAM075BDE, DGAM075BDF, DGAT070BDD, DGAT070BDE, DGAT070BDF, DGAT075BDD, DGAT075BDE, DGAT075BDF, DLAS075BDD, DLAS075BDE, DLAS075BDF.
Consumers should immediately stop using the furnace until it has been inspected and repaired. Consumers should contact UPG to schedule a free inspection and repair of any furnace involved in the recall.
For more information, including information about installation issues that may lead to the hazard, contact UPG toll-free at 888/665-4640 between 8 a.m. and 5 p.m. CT Monday through Friday or visit its website at www.dgatprogram.com. UPG Technical Services is also conducting a comprehensive notification and communications program and working with its distributors to locate owners.
To see pictures of the recalled product, visit www.cpsc.gov/cpscpub/prerel/prhtml12/12102.html or http://cpsr-rspc.hc-sc.gc.ca/PR-RP/recall-retrait-eng.jsp?re_id=1416.